8 Jul electrical specifications of ASTM F . Ground cable assemblies shall have an ampacity greater than or equal to that of No. 2 AWG copper. ASTM Standard F was originally written with the intent of covering temporary protective grounds to be used on overhead power lines. The standard was bas. Abstract– During implementation of a maintenance program that was intended to check compliance of field grounding devices with ASTM F, field personnel.
|Published (Last):||8 August 2016|
|PDF File Size:||18.97 Mb|
|ePub File Size:||13.7 Mb|
|Price:||Free* [*Free Regsitration Required]|
That is where preambles to the standards, interpretations, CPLs and consensus standards are needed. Assemblies that have been subjected to these shall not be re-used. Type III is astm f855 installed using a formed T-handle astm f855 is intended as a first astm f855 to a system neutral, pole astm f855, or grounded station or apparatus steel that does not require use of a hot stick. For this article, we revised the astm f855 according to the revision of F Train the Trainer Be the first to submit a comment.
Good information and effective training are key to maintenance and continued improvement in this high level of workplace safety performance. Plain copper ferrules are usually used with bronze clamps. TPG testing is done on complete assemblies. They were placed on your computer when you launched this website. Not Logged In Member?: This standard does not purport to address all of the safety concerns, if any, associated with its use. These specifications for a system of protective grounding utilizing copper cables are covered in four parts, as follows: Ferrule Types Ferrules are categorized according to ferrule-to-clamp connection method and by either shrouded astm f855 nonshrouded.
It is not permissible to make a stranded conductor connection directly to a clamp. These initial fault current levels are the basis for the differences in the 6-,and cycle ratings of the grounding system components. The nonthreaded stud connector of an ASTM-rated ferrule is always half-diameter size for astm f855 grade even though each grade of ferrule corresponds to a specific cable size.
If the v855 is improperly rated and fails before the system protection opens, the fault current will take any other available path, which includes personnel in astm f855 with the faulted conductor. Most manufacturers will not use nonstandard cables in delivered assemblies.
This abstract is astm f855 brief summary of the referenced standard. It is the responsibility of the user of this standard to establish appropriate safety, astm f855, and environmental practices and determine the applicability of regulatory limitations prior to use.
Assembly ratings assume the grade of lowest graded component see This method is commonly referred to as the infinite buss theory.
Clamps for Temporary Protective Astm f855. A nut on either side of the terminal is tightened to trap the ferrule in place.
Astm f855 25 years as a transmission distribution lineman and foreman, Jim Vaughn has devoted the last 15 years to safety and training. Conclusion Over the years the utility industry has recognized that personal protective grounding has saved many lives. At present, there is no Type II asmt. He can be reached at This email address is being protected from spambots.
There are no restrictions for using either copper or aluminum ferrules on high-flexibility ASTM-compliant copper grounding cable. The DC astm f855 asymmetry drops off quickly because of I2r losses in the circuit. Each of the four parts is an entity astm f855 itself, but is listed as a part of the system for completeness and clarification.
About Astm f855 Grounds assembled by the employer require continuity integrity testing and inspection in order to comply with Resistance in the protective ground increases current across the worker in a fault.
A noted author, trainer and lecturer, he is director of safety for Atkinson Power.
astm f855 All clamps require a ferrule-to-terminal connection. The principal difference in each type is the temperature rating of the insulation and stranding of the conductor.
That is accomplished using a broad array of tools and rules for astm f855 employer and workforce. It is the responsibility of the user of this standard to establish appropriate safety, asfm, and environmental practices and determine the applicability of regulatory limitations prior to use. In addition, the paragraph notes that many of these cables have been tested to the ASTM standard and qstm been found to meet the requirements of the standard.
Current astm f855 Grounds Can Kill. Most of the cables in the market are constructed to ASTM standards and have performed well in utility use. See Appendix Asfm for details.